Fault test cases for series compensated transmission line with the capacitor at the middle of the line
type: Dataset
description: Description This data set contains time series data of different simulated fault cases in high voltage series compensated transmission lines. The simulation is done in PSCAD using the Python automation library. The capacitor is located in the middle of the line. The model of the line is given in the attached pdf file. The CT and VT are located at bus S. The distance are counted from bus S. The modelled line is 500 kV and 200 km long. The simulation is run for 1 second with 10 kHz sampling rate. Each file contains 10 data in the following order, Time Voltage phase A Voltage phase B Voltage phase C Current phase A Current phase B Current phase C Voltage across capacitor phase A Voltage across capacitor phase B Voltage across capacitor phase C The variables used to study different test cases are shown below, Fault inception angle (referred to phase A voltage): 0 and 90 degree Source impedance ratio: 0.20 and 0.35 Capacitor compensation level: 94 µF(50%), 78 µF(60%), 67 µF(70%) Fault resistance: 0.10, 10, 20 ohm Fault location: 10 km, 30 km, 50, 70 km, 90 km, 95 km, 105 km, 110 km, 130 km, 150 km, 160 km, 170 km, 180 km Fault type: No-fault, AG, BG, CG, ABG, CAG, BCG, ABCG, AB, CA, BC, ABC All these factors lead to 5616 test cases in total. The test cases are organized in four (4) zipped folders each containing 1404 test cases. The PSCAD model file and an example python script that can be used to automate the simulations are also included herewith for anyone interested to replicate the results. The name of the folders contains the information regarding fault inception angle and source impedance ratio for all test cases inside that folder, for example, the folder name Outputs_0_0.20 can be decoded as, 0: Fault inception angle (phase A) 0.20: Source impedance ration The files names inside the folders include information about the other variables used in generating the test case. For example, the name test_f_10_0_67_0.01 can be interpreted as, test_f: f for forward fault 1…
conditions of access: http://publications.europa.eu/resource/authority/access-right/PUBLIC
conditions of access: info:eu-repo/semantics/openAccess
creative work status: completed
  type: DefinedTerm
  in defined term set: http://publications.europa.eu/resource/authority/dataset-status
  term code: COMPLETED
creator: Md Tanbhir Hoq
date modified: 2024-07-17
date published: 2021-11-03
language: English
is part of: https://zenodo.org/communities/kth/
keywords: Electrical Engineering, Electronic Engineering, Information Engineering
  type: DefinedTerm
  term code: 202
keywords: series capacitor
keywords: fault data
keywords: time series
keywords: transmission line
keywords: protection
keywords: power system protection
license: https://creativecommons.org/licenses/by/4.0/
publisher: Royal Institute of Technology
version: 0

PropertyValue
property ID: DOI
value: 10.5281/zenodo.5643563

PropertyValue
property ID: URL
value: https://zenodo.org/records/5643563

PropertyValue
property ID: oai
value: oai:zenodo.org:5643563

Md Tanbhir Hoq
type: Person
affiliation: KTH The Royal Institute of Technology
family name: Md Tanbhir Hoq

English
type: Language
alternate name: eng

Royal Institute of Technology
type: Organization